Thanks to our experience of over 45 years in the LPG industry our expertise is unrivalled and our services for complete technical installation assure the fair, efficient and economical operation of the installation by trained and certified technicians who make the process expedited and hassle-free. And with all the relevant safety certifications in place, you are guaranteed safety and quality to the highest standards from both an aesthetic and functional perspective with Intergaz.
The first stage of the LPG bulk storage tank installation involves a visit from an experienced and qualified Intergaz technician to your house or business premises. Once we have reviewed your premises, we offer advice regarding the most appropriate tank size for your requirements; the most suitable location considering all the aspects of your site (from practicality to aesthetics), and the most suitable tank position in conformity with safety regulations and for your better safety, as well as to provide easy access for Intergaz LPG tanker (refilling) vehicles.
Get in touch with Intergaz Customer Service or submit your request electronically
A site visit from an Intergaz experienced and qualified technician to your home or business premises, is arranged.
We design any installation around your requirements and always in full compliance with legal requirements.
The installation of the tank can be completed within one day. We deliver the tank to your site often using a crane to lift and place the tank on its concrete pad
After Sales Services
Intergaz Technical Service team is available 24 hours a day, 7 days a week. Contact us for your inspection request and other needs
A professional LPG Bulk Installation consists of the following:
- Storage tank
- Piping arrangement
- Safety equipment
- Pressure accessories
- Sprinkler system
- Consumption devices
Intergaz installations of bulk tanks are in full compliance with European and local regulations and all procedures are thoroughly followed to enable the reliable distribution and usage of LPG that meets Health & Safety standards.
Cyprus Legislative Safety Distances:
Maximum tank water capacity (litres);
Maximum water capacity of a group of tanks(litres)
Minimum distances in meters
From buildings, boundaries, fixed source of ignition or group of tanks.
At or above ground
At or above ground
Up to 500
Once a suitable tank location is found the site must be appropriately prepared for the tank installation. The installation of the tank can be undertaken in one day.
Intergaz technicians will carry out the last safety checks and will explain everything that you should know about the tank.
As a new customer, you will receive important information regarding customer service, ordering of LPG, cost/payment, and safety measures.
All LPG tanks must be placed at an external ground-level location with all necessary equipment that satisfies the following requirements:
Keeps safety distances as defined by governmental regulations.
Should not be close to exiting doors.
Should have a solid and flat concrete ground base and located away from dangerous areas.
There should be no dirt, dry grass, plants, volatile and explosive materials etc, within a three-metre radius of the LPG tank.
The LPG tank should not be close to any underground locations, openings, underground ventilation units, sewers, and building openings.
The area between the building and the storage location of the tank needs to be made from non-combustible materials.
The storage location of the tank should be protected by a metallic cover. In addition, it is preferable that the tank’s sides are also protected using a non-flammable fence (height of two metres). Such a fence should be able to stop unauthorised people from accessing the tank. The fence should, however, permit the ventilation of the ground and the tank’s sides (as mentioned above). Ground ventilation is required in order to enhance the evaporation of LPG in the unusual situation of a leak.
There should be an independent earthing system.
Finally, the opinion of the Fire Department is of great importance and should be taken into account during the process of selecting a suitable storage site for LPG.
Note: Customer is expected to undertake the above-mentioned preparation themselves, but we are always available for guidance and to offer advice and support.
After Tank Installation:
- Keep rubbish, ragweed, grass, and any combustible materials away from the tank. Maintain a suitable metal fence and keep a three-metre radius from the LPG tank clean at all times.
- Keep vehicles, electrical equipment, smoking and any other sources of ignition well away from the installation.
- Do not make any alterations within the specified (by law) perimeter of the tank which may affect the installation. Contact Intergaz for advice.
Only allow Intergaz or those authorised by Intergaz have access to the installation.